Ball valves can be defined as the opening and closing member (ball) driven by the stem, and rotational movement around the axis of the ball valve valve. They can also be used for fluid regulation and control. The hard-sealed V-ball valve has a strong shear force between the V-ball core and the metal seat of the welded carbide, especially suitable for media containing fibers, tiny solid particles, etc.. While the multi-way ball valves in the pipeline not only can flexibly control the media merging, diverging, and switching of flow direction, but also can close any channel and connect the other two channels. This type of valve in the pipeline should generally be installed horizontally. Ball valves is divided into: pneumatic ball valves, electric ball valves and manual ball valves according to the drive mode.
In a half-open state, one end of the valve introduced into test media, and the other end is closed; Turn the ball several times, then check the closed end of valve in the state of closing, as well as the packing and gasket sealing performance preventing from leakage. Then introduces the test medium from the other end, repeating the above test.
Rotate ball in the closing state several times before the test, introducing the test medium to the specified value from one end; use the pressure gauge (accuracy 0.5 ~ 1 level) to check the sealing performance of the introduction end, with the range of the test pressure 1.5 times. In the specified time, it is qualified without phenomenon of pressure drop; and then introduce the test medium from the other end, repeating the above test. Then, put the valve in a half-open state with both ends closed and the cavity filled with media, checking the packing and gasket at the test pressure without leakage.
Check valves are automatically opened and closed by the force which is generated by the flow of the medium in the pipeline. Check valves used for pipeline system prevent the backflow of media, the pump and drive motor reversal, as well as the release of container media. They can also be used to provide recharge to the auxiliary system in which the pressure may rise above the system pressure, which mainly can be divided into rotary (rotating according to the center of gravity) and lift (moving along the axis).
The opening and closing part as circular valve disc relies on its own weight and medium pressure to produce action to block the backflow of the medium.
Scope of Application
Fire pump discharge pipe, high level fire water tank discharge pipe, pressure stabilization pump discharge pipe, pump splicer and other locations.
Supplementary note: It includes the anechoic check valve and water hammer elimination check valve. Measures are set up inside the valve body to reduce the sound of the valve flap impact when the valve is closed and eliminate water hammer.
Check Valve Pressure Test Method
Check Valve Test State
The disc axis of lift check valve is vertical, while swing check valve channel axis and disc axis in a position approximately parallel to the horizontal line.
When strength test, the introduction of test media from the inlet end to the specified value, the other end closed, make sure the valve body and valve cover no leakage for qualified.
Introduce test media from the outlet side at the inlet end to check the sealing surface, packing and gasket at no leakage for qualified.